Method of Operation
In STERILAIRE™ Room Air Sanitizers room air is drawn past washable electrostatic filters, then forced into an ultraviolet exposure chamber in which the air is subjected to powerful germicidal rays, past baffles and then reintroduced into the room.
The STERILAIRE Room Air Sanitizer provides effective germicidal treatment without the hazards associated with exposed ultraviolet lamps. Application of equipment is simple and straightforward.
In selecting your STERILAIRE Room Air Sanitizer several factors should be considered.
STERILAIRE Room Air Sanitizers are selected to treat a given area based on the equipment room air changes per hour that the STERILAIRE Room Air Sanitizer is capable of treating.
To treat areas that are normally or well ventilated, we recommend selection of a STERILAIRE Room Air Sanitizer that will yield a minimum of three (3) equivalent room air changes per hour.
In areas that are poorly ventilated and areas that present a higher than usual risk of airborne infection (such as a crowded waiting room), installation of a STERILAIRE Room Air Sanitizer capable of six (6) equivalent room air changes per hour is recommended.
To select the appropriate STERILAIRE Room Air Sanitizer(s), first determine the desired number of equivalent room air changes per hour. Then calculate the total cubic feet per hour required to yield the desired number of equivalent room air changes using the following formula:
Room Size (cubic feet) x Room Air Changes = Cubic Feet per Hour
Once the volume of the area to be treated is known, Tables 1 and 2 can be used to select the most suitable STERILAIRE Room Air Sanitizer for your application.
|MODEL||NOMINAL MAXIMUM TREATMENT CAPACITY|
|MODEL 2 – RS||3600 CUBIC FEET PER HOUR|
|MODEL 3 – RS||8400 CUBIC FEET PER HOUR|
|MODEL 6 – RS (LOW SPEED)||17,700 CUBIC FEET PER HOUR|
|MODEL 6 – RS (HIGH SPEED)||26,100 CUBIC FEET PER HOUR|
|MODEL||BLOWER CAPACITY||MAXIMUM ROOM SIZE TREATED 0.3 ROOM AIR CHANGES/HOUR||MAXIMUM ROOM SIZE TREATED 0.4 ROOM AIR CHANGES/HOUR||MAXIMUM ROOM SIZE TREATED 0.5 ROOM AIR CHANGES/HOUR||MAXIMUM ROOM SIZE TREATED 0.6 ROOM AIR CHANGES/HOUR|
|2 – RS||60 CFW||1200 CUBIC FEET||900 CUBIC FEET||720 CUBIC FEET||600 CUBIC FEET|
|3 – RS||140 CFW||2800 CUBIC FEET||2100 CUBIC FEET||1680 CUBIC FEET||1400 CUBIC FEET|
|6 – RS||435 CFW||8700 CUBIC FEET||8525 CUBIC FEET||5220 CUBIC FEET||4350 CUBIC FEET|
Standard unit shown above includes free standing rubber feet – See Optional Mounting Bracket Sheet for optional painted finish.
Total electrical requirement: 1.0 amp, 115V 50/60 Hz
Unit weight: 24 lbs.